Post by Christopher on Dec 29, 2009 14:48:46 GMT -6
What do all these settings mean?
There are really only a couple settings you might want to change. These are as follows:
J0: This will change between farenheit and celcius. J5: Turning this on will cause the circulator to run for one minute every three days. This helps to maintain pump lubrication in times when the system is off. J6: Here is where you can select between Air temperature and Flr (Floor) temperature. Air mode will try to maintain the selected air temperature, while keeping the floor temperature between it's low and high limits. Floor mode will simply hold a selected floor temperature. FL: When in Air mode, this is where you will set the low temperature limit of your floor. FH: When in Air mode, this is where you will set the high temperature limit of your floor.
To see the full list of settings, you can download the PDF here.