Post by bryansemple on Jan 31, 2013 18:45:37 GMT -6
I have a Watts dual temp thermo stat. The settings allow for a timer to control the thermostat and set it back when 24 VAC is applied (at least that is what I believe based on an older instruction sheet I found). But the current instructions do not list where to apply this 24 VAC to enable setback. Can someone provide the wiring instructions for where to connect this?
Just wondering if you ever figured out if in fact it was a 24 vac signal? I sent one to my thermostat and it did switch it to the set back but it also through off the temperature reading due to a resister getting hot. thermostat read about 2 deg. f above actual temp.